Sometimes during transformer infrared inspection or during a GA oil analysis problems are found.
Bushing Well Insert Problem
If you don’t fix transformer issues found during your infrared inspection you might find yourself doing this!
Transformer problem areas can include the following internal parts:
- HV Cable
- Loadbreak Insert
- Bushing Well
- Oil in the Transformer Front
- Current Limiting Fuses
All transformer repairs require at least 8 hours of outage.
Draining the Transformer Oil
Changing out Internal Parts
Some transformer fixes require draining the DGA oil so the transformer’s internal parts like current limiting fuses or expulsion fuses can be changed out.
Current Limiting Fuses
All-Test can help you with infrared inspections and transformer maintenance & repair.